4 large axial extract fans caused noise complaints over a wide area in Canada, despite multiple attempts at noise control based on conventional techniques. One email led to the noise being reduced by 99% with no site visits required - the whole project was completed over the internet.
Mitchell, the site engineer sent us an email with smartphone video clips and photos. Sound track analysis showed the problem to be high level tones at the 197Hz blade pass and harmonics. We used the photos to design retro-fit aerodynamic noise reducing components which the client made and installed to give 20dB attenuation at 100m.
"We are exceptionally happy with the overall results that were obtained, from a noise reduction, cost, and time stand point. INVC was very professional and prompt on all deliverables. Out of all solutions attempted this was by far the best and cost effective. The whole process was very smooth from first contact to installation … glad we went with INVC, thanks…"
In addition to the noise reduction, the performance of the fans was also improved which means that the project will pay for itself in reduced running costs.